Water Supply Industry Interpretations and Advice
- Area of Interest : WCs
- Topic : Warning pipe
- Title : WC cisterns - inappropriate use
- Clause Reference : Regulation 3 & Schedule 2 paragraph 25 (1)(h): G25.8
- Reference Number : WC02
- Decision Date : June 2001
Disposal of condensate water via a WC cistern and internal warning pipe (overflow) to a WC pan could be mistaken for a warning discharge and is not acceptable.